/**
 * @file
 * @author Steve Karg <skarg@users.sourceforge.net>
 * @date 2006
 * @brief A basic BACnet Binary Input Object implementation.
 * Binary Input objects are input objects with a present-value that
 * uses an enumerated two state active/inactive data type.
 * @copyright SPDX-License-Identifier: MIT
 */
#ifndef BACNET_BASIC_OBJECT_BINARY_INPUT_H
#define BACNET_BASIC_OBJECT_BINARY_INPUT_H
#include <stdbool.h>
#include <stdint.h>
/* BACnet Stack defines - first */
#include "bacnet/bacdef.h"
/* BACnet Stack API */
#include "bacnet/cov.h"
#include "bacnet/rp.h"
#include "bacnet/wp.h"

#if (INTRINSIC_REPORTING)
#include "bacnet/basic/object/nc.h"
#include "bacnet/getevent.h"
#include "bacnet/alarm_ack.h"
#include "bacnet/get_alarm_sum.h"
#endif

/**
 * @brief Callback for gateway write present value request
 * @param  object_instance - object-instance number of the object
 * @param  old_value - binary preset-value prior to write
 * @param  value - binary preset-value of the write
 */
typedef void (*binary_input_write_present_value_callback)(
    uint32_t object_instance,
    BACNET_BINARY_PV old_value,
    BACNET_BINARY_PV value);

#ifdef __cplusplus
extern "C" {
#endif /* __cplusplus */

BACNET_STACK_EXPORT
void Binary_Input_Property_Lists(
    const int **pRequired, const int **pOptional, const int **pProprietary);

BACNET_STACK_EXPORT
bool Binary_Input_Valid_Instance(uint32_t object_instance);
BACNET_STACK_EXPORT
unsigned Binary_Input_Count(void);
BACNET_STACK_EXPORT
uint32_t Binary_Input_Index_To_Instance(unsigned index);
BACNET_STACK_EXPORT
unsigned Binary_Input_Instance_To_Index(uint32_t instance);
BACNET_STACK_EXPORT
bool Binary_Input_Object_Instance_Add(uint32_t instance);

BACNET_STACK_EXPORT
bool Binary_Input_Object_Name(
    uint32_t object_instance, BACNET_CHARACTER_STRING *object_name);
BACNET_STACK_EXPORT
bool Binary_Input_Name_Set(uint32_t object_instance, const char *new_name);
BACNET_STACK_EXPORT
const char *Binary_Input_Name_ASCII(uint32_t object_instance);

BACNET_STACK_EXPORT
BACNET_BINARY_PV Binary_Input_Present_Value(uint32_t object_instance);
BACNET_STACK_EXPORT
bool Binary_Input_Present_Value_Set(
    uint32_t object_instance, BACNET_BINARY_PV value);

BACNET_STACK_EXPORT
const char *Binary_Input_Description(uint32_t instance);
BACNET_STACK_EXPORT
bool Binary_Input_Description_Set(uint32_t instance, const char *new_name);

BACNET_STACK_EXPORT
BACNET_RELIABILITY Binary_Input_Reliability(uint32_t object_instance);
BACNET_STACK_EXPORT
bool Binary_Input_Reliability_Set(
    uint32_t object_instance, BACNET_RELIABILITY value);

BACNET_STACK_EXPORT
const char *Binary_Input_Inactive_Text(uint32_t instance);
BACNET_STACK_EXPORT
bool Binary_Input_Inactive_Text_Set(uint32_t instance, const char *new_name);

BACNET_STACK_EXPORT
const char *Binary_Input_Active_Text(uint32_t instance);
BACNET_STACK_EXPORT
bool Binary_Input_Active_Text_Set(uint32_t instance, const char *new_name);

BACNET_STACK_EXPORT
BACNET_POLARITY Binary_Input_Polarity(uint32_t object_instance);
BACNET_STACK_EXPORT
bool Binary_Input_Polarity_Set(
    uint32_t object_instance, BACNET_POLARITY polarity);

BACNET_STACK_EXPORT
bool Binary_Input_Out_Of_Service(uint32_t object_instance);
BACNET_STACK_EXPORT
void Binary_Input_Out_Of_Service_Set(uint32_t object_instance, bool value);

BACNET_STACK_EXPORT
unsigned Binary_Input_Event_State(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Encode_Value_List(
    uint32_t object_instance, BACNET_PROPERTY_VALUE *value_list);
BACNET_STACK_EXPORT
bool Binary_Input_Change_Of_Value(uint32_t instance);
BACNET_STACK_EXPORT
void Binary_Input_Change_Of_Value_Clear(uint32_t instance);

BACNET_STACK_EXPORT
int Binary_Input_Read_Property(BACNET_READ_PROPERTY_DATA *rpdata);
BACNET_STACK_EXPORT
bool Binary_Input_Write_Property(BACNET_WRITE_PROPERTY_DATA *wp_data);
BACNET_STACK_EXPORT
void Binary_Input_Write_Present_Value_Callback_Set(
    binary_input_write_present_value_callback cb);

BACNET_STACK_EXPORT
bool Binary_Input_Write_Enabled(uint32_t instance);
BACNET_STACK_EXPORT
void Binary_Input_Write_Enable(uint32_t instance);
BACNET_STACK_EXPORT
void Binary_Input_Write_Disable(uint32_t instance);

BACNET_STACK_EXPORT
void *Binary_Input_Context_Get(uint32_t object_instance);
BACNET_STACK_EXPORT
void Binary_Input_Context_Set(uint32_t object_instance, void *context);

BACNET_STACK_EXPORT
uint32_t Binary_Input_Create(uint32_t object_instance);
BACNET_STACK_EXPORT
bool Binary_Input_Delete(uint32_t object_instance);
BACNET_STACK_EXPORT
void Binary_Input_Cleanup(void);
BACNET_STACK_EXPORT
void Binary_Input_Init(void);

#if defined(INTRINSIC_REPORTING) && (BINARY_INPUT_INTRINSIC_REPORTING)
BACNET_STACK_EXPORT
bool Binary_Input_Event_Detection_Enable(uint32_t object_instance);
BACNET_STACK_EXPORT
bool Binary_Input_Event_Detection_Enable_Set(
    uint32_t object_instance, bool value);

BACNET_STACK_EXPORT
int Binary_Input_Event_Information(
    unsigned index, BACNET_GET_EVENT_INFORMATION_DATA *getevent_data);

BACNET_STACK_EXPORT
int Binary_Input_Alarm_Ack(
    BACNET_ALARM_ACK_DATA *alarmack_data, BACNET_ERROR_CODE *error_code);

BACNET_STACK_EXPORT
int Binary_Input_Alarm_Summary(
    unsigned index, BACNET_GET_ALARM_SUMMARY_DATA *getalarm_data);

BACNET_STACK_EXPORT
uint32_t Binary_Input_Time_Delay(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Time_Delay_Set(uint32_t object_instance, uint32_t time_delay);

BACNET_STACK_EXPORT
uint32_t Binary_Input_Notification_Class(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Notification_Class_Set(
    uint32_t object_instance, uint32_t notification_class);

BACNET_STACK_EXPORT
BACNET_BINARY_PV Binary_Input_Alarm_Value(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Alarm_Value_Set(
    uint32_t object_instance, BACNET_BINARY_PV value);

BACNET_STACK_EXPORT
uint32_t Binary_Input_Event_Enable(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Event_Enable_Set(
    uint32_t object_instance, uint32_t event_enable);

BACNET_STACK_EXPORT
BACNET_NOTIFY_TYPE Binary_Input_Notify_Type(uint32_t object_instance);

BACNET_STACK_EXPORT
bool Binary_Input_Notify_Type_Set(
    uint32_t object_instance, BACNET_NOTIFY_TYPE notify_type);
#endif

BACNET_STACK_EXPORT
void Binary_Input_Intrinsic_Reporting(uint32_t object_instance);

#ifdef __cplusplus
}
#endif /* __cplusplus */
#endif
